by Grant Lobdell
Dyne is excited to be featured in the Jan/Feb 2022 issue of Sprinkler Age magazine
The article How to Take a Representative Sample - Sampling Sprinklers for NFPA 25 Field Service Testing is found on pages 24-25. Dyne also has an ad on page 29.
Defining the Sample Area
NFPA 25 does not define the sample area. Upon the decision to test instead of replace, the sample area is to be determined by the building owner in consultation with their designated representative, if applicable. Sample areas can be as large or as small as desired. When determining the sample area, the building owner and/or their designated representative will want to consider a variety of factors including, but not limited to, the environment the sprinklers are in and the cost of testing versus replacement.